Within This Page
- Operation and Maintenance
- Special Considerations
- Additional Resources
Hydropower is the most common renewable energy technology. Humans have been harnessing water to perform work for thousands of years. For example, more than 2,000 years ago, the Greeks used water wheels for grinding wheat into flour. Hydropower uses the gravitational force of water to turn turbines and generate electricity. The size of the hydroelectric plant is directly related to the amount and flow of water. There are three types of hydropower facilities: run-of-the-river (otherwise known as hydrokinetic or diversion), impoundment, and pumped storage.
Current interest in hydropower has been primarily directed at developing incremental hydropower by using an existing dam. This includes new hydroelectric generation capacity achieved by increased efficiency or additions of new capacity at an existing hydropower project. This also includes new electric generation projects that are run-of-the-river projects, particularly at existing non-power dams.
This section focuses primarily on run-of-the-river hydroelectric systems under 5 megawatts (MW) implemented at an existing dam. Other systems are not likely to be used in conjunction with a Federal construction project.
A run-of-the-river hydroelectric system is made up of several key components including:
- Penstock or water conveyance
- Turbine, pump, or wheel
- Turbine shaft
- Alternator or generator.
A portion of a river's water is diverted to a water conveyance, a channel, pipeline, or pressurized pipeline, called a penstock. The water is either filtered before or after entering the penstock to remove the accumulated debris before it is delivered to a powerhouse encasing a turbine, pump, or wheel. The moving water rotates the wheel or turbine, spinning the turbine shaft. This motion can be used for mechanical processes, or to power an alternator or generator to create electricity.
Types of Technology
The following provides information on the three main types of hydropower technology.
A run-of-the-river system diverts a portion of a river's water to a turbine or wheel. Diversion systems can be put in place with an existing dam that does not have a reservoir. For Federal facilities that are located near an existing dam, this type of system may present a predictable, cost-effective renewable electricity option.
An impoundment facility uses a dam to store river water in a reservoir. Impoundment facilities are typically large-scale hydropower plants, which produce large amounts of electricity for electric utility projects or the government. These systems are synonymous with hydropower in the public's mind, and range from projects around 30 MW to massive projects such as the Hoover Dam. Dams have a significant impact on the ecosystem, thus, the National Hydropower Association forecasted a decline in large-scale hydropower use through 2020. This is a not a feasible technology for Federal facilities to implement into new construction or major renovation projects, but sites could purchase their electricity from an existing large-scale hydroelectric plant in the vicinity.
The following items qualify as renewable energy for meeting the Energy Policy Act of 2005 requirement for Federal facilities:
- Incremental hydropower includes efficiency increases in existing units and/or by the addition of capacity to utilize flow for generation that would otherwise be spilled at existing dams.
- Run-of-the-river used as electricity. Due to a streamlined approval process, the best applications for this technology are projects up to 5 MW at existing non-power dams.
The economics of hydroelectric power can be very favorable, since the energy is predictable and available on a continual basis. However, until recently, the licensing of even small systems, which is handled by the Federal Energy Regulatory Commission (FERC), required the same process as full-size impoundment dams. In 2010, FERC streamlined the rules for systems up to 5 megawatts at existing dams. More details are available from the Small/Low Impact Hydropower Program run by FERC.
Cost estimates are not yet available under this new approval process, but are expected to be cost effective in some cases. There are a variety of financial incentives available for hydropower, including: income tax credits, property tax exemptions, state sales tax exemptions, loan programs, and special grant programs. More information is available at the Database of State Incentives for Renewables & Efficiency (DSIRE).
Many incentives may not be available to Federal agencies, but renewable energy project funding options may be available to monetize these incentives and improve system economics.
The Federal Energy Management Program (FEMP)'s Guide to Integrating Renewable Energy in Federal Construction has more information on renewable energy project funding.
Assessing Resource Availability
Only 3% of the nation's 80,000 dams currently generate electricity, and these present a significant renewable energy resource without the environmental concerns of impoundment facilities. In fact, by 2025, 10,000 MW of energy could be gained by converting non-powered dams.
For run-of-the-river systems, applications under the streamlined FERC guidelines need to be located at an existing dam. Not all dams will be likely targets for electricity production, since the amount of power that can be obtained from a stream or river depends on the amount of water flow, the height at which the water falls, and the efficiency of the plant to convert mechanical energy to electrical energy. The National Inventory of Dams is a collection of information about dams in the United States and its territories, produced by the U.S. Army Corps of Engineers.
In March 2011, the Bureau of Reclamation completed a hydropower resource assessment to study the economic viability of adding hydropower development to existing reclamation facilities. The study concluded that out of 530 sites studied, the department could generate up to 1 million megawatt-hours of electricity annually by adding hydropower capacity at 70 of its existing facilities located in 14 states. In October 2010, a similar study was completed to assess the potential capacity increases at existing hydropower plants .
To determine if a small hydropower system is appropriate, consult the National Renewable Energy Laboratory's (NREL) publication on Small Hydropower Systems .
In preparing conduit and 5-MW exemption applications, applicants should follow section 4.38(b) of FERC's regulations. If applying for a license, there are three processes available: integrated licensing process, traditional licensing process, and alternative licensing process. Many small hydropower developers prefer to use FERC's traditional licensing process because it has fewer defined pre-filing steps and deadlines than the integrated licensing process, has a more informal study development process, and does not require the formation of a collaborative workgroup like the alternative licensing process.
After considering the energy resource, providing sufficient information in the application will help speed the FERC process. Therefore, be sure to:
- Document the rights needed for project construction and operation
- Take advantage of existing information on environmental resources in the project area
- Address any issues that have been identified.
Also, be sure to conduct adequate consultation, including:
- Identifying the key Federal and state agencies, tribes, and citizen groups likely to have an interest in the project
- Meeting with the stakeholders as soon as possible in the planning process
Operation and Maintenance
The operation and maintenance (O&M) costs of hydropower are between 1.5% and 2.5% of investment cost per year. The water intake, water conduit system, and associated equipment are all vital to the functionality of the hydropower plant. Cavitation and erosion should be monitored, and regular inspection of runners of turbines should be carried out and recorded.
The following are important special considerations for hydropower systems.
Producing power can lead to selling excess power to the local utility. Contact the local utility for the facility to find out about application procedures, metering and rates, and the equipment the utility requires to connect the system to the grid. More detailed information on net-metering for hydropower is available in NREL's publication on Small Hydropower Systems .
FEMP's Guide to Integrating Renewable Energy in Federal Construction has more information on interconnection requirements and net-metering.
Net metering laws often specify which technologies qualify, and not all will include hydropower. In addition, all hydropower facilities are licensed by FERC, instead of the state public utility commission. Because FERC has just recently streamlined the process for small hydropower facilities, the market is expanding for these types of technologies, but not all utility considerations and jurisdictional issues have been resolved. Interconnection of the facility may be governed by state rules or via Federal requirements, such as the Public Utility Regulatory Policies Act of 1978, which allow for interconnection but provide less economic incentive for a project.
- FERC issues licenses for the construction of a new project, or the continuance of an existing project (relicensing); and provides oversight of all ongoing project operations, including dam safety inspections and environmental monitoring.
- National Inventory of Dams is a collection of information about dams in the United States and its territories, produced by the U.S. Army Corps of Engineers.
- Hydropower Systems by DOE
- Assessment of Potential Capacity Increases at Existing Hydropower Plants by the Bureau of Reclamation